Turbo korpus wentylatora
- high air exchange capacity
- ABS plastic
- ball bearings
- maximum operating temperature 40°C
- wall and ceiling installation allowed*
- 5 years warranty
- non-return valve (ZZ) usage ability
Escudo PEGR P
Escudo PEGB P
Escudo PEGR M
Escudo PEGB M
Trax PTGR P
Trax PTGB P
Trax PTGR M
Trax PTGB M
Trax PTGG M
The Easy Clip system allows easy assembly and disassembly of the fan front panel without using tools. Which significantly reduces the time of installation and maintenance of the device.
The fan is switched on and off by means of a switch (not included in the device) being a part of the building’s electrical system.
The fan is on and off by means of a cord switch by a single pull.
The fan is switched on and off by means of a switch (not included in the device) being a part of the electrical installation of the building, but it will turn off after the time set by a potentiometer on the PCB has elapsed. The minimum delay is 3 minutes, the maximum - 30 minutes. Time delay adjustment is smooth.
The humidity sensor detects moisture in the range of 40% to 90% relative humidity. The fan – depending on the connection solution to the network – can be launched automatically or manually. AUTOMATIC START: the device switches on when the air humidity level exceeds the value set on the H-potentiometer and it switches off after passage of time (defi ned on the T-potentiometer) counted from the moment of humidity level decerease.
MANUAL START: the fan is activated by the switch being part of the building’s electrical system (not included in the device) or a separate switch intended for fan. After turning off the switch, the device (as in the fi rst case) switches off after the time specifi ed on the T-potentiometer, if the moisture level in the room is below the level set on the H-potentiometer. The moisture detection system is the master system.
The fan starts automatically when any motion in the room where it is installed is detected. It turns off after the last – registered by the detector – movement with adjustable delay. The motion detector sensivity can be adjusted by a potentiometer located on the PCB. Time delay adjustment is a smooth regulation from 3 to 30 minutes. The controller has the largest reception in fans with plastic panels. In case of glass panels, its sensitivity decreases approximately by 20%. Do not use metal panels in this equipment option.
The Control equipment option allows for adjusting the speed level, hence the fan operation parameters (capacity, power consumption, volume level), so as the the time delay. Adjustment of the timer is available in two modes: minute (5, 10, 20 and 30 min.) and hour mode (from 1 to 10 hours in intervals of one hour). The buttons located at the bottom of the fan are used for programming.