Trax panel fan
- ABS plastic
- ball bearings
- maximum operating temperature 40°C
- ceiling installation allowed
- 5 years warranty
- non-return valve (ZZ) usage ability
The Easy Clip system allows easy assembly and disassembly of the fan front panel without using tools. Which significantly reduces the time of installation and maintenance of the device.
The fan is switched on and off by means of a switch (not included in the device) being a part of the building’s electrical system.
The fan is on and off by means of a cord switch by a single pull.
The fan is switched on and off by means of a switch (not included in the device) being a part of the electrical installation of the building, but it will turn off after the time set by a potentiometer on the PCB has elapsed. The minimum delay is 3 minutes, the maximum - 30 minutes. Time delay adjustment is smooth.
The humidity sensor detects moisture in the range of 40% to 90% relative humidity. The fan – depending on the connection solution to the network – can be launched automatically or manually. AUTOMATIC START: the device switches on when the air humidity level exceeds the value set on the H-potentiometer and it switches off after passage of time (defi ned on the T-potentiometer) counted from the moment of humidity level decerease.
MANUAL START: the fan is activated by the switch being part of the building’s electrical system (not included in the device) or a separate switch intended for fan. After turning off the switch, the device (as in the fi rst case) switches off after the time specifi ed on the T-potentiometer, if the moisture level in the room is below the level set on the H-potentiometer. The moisture detection system is the master system.
To indicate a model in a specific color, add the letter designation of a given color to the index: